CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
|Published (Last):||28 October 2018|
|PDF File Size:||2.83 Mb|
|ePub File Size:||7.43 Mb|
|Price:||Free* [*Free Regsitration Required]|
I’ve made mistake, because communication module is diffirent than I mentioned before. Here I have que diagnostic of the cp slave.
myOMRON Europe: Services & Support
Hello, the BF led blink in the omron master, the slave appear only with the led run. I don’t have this software installed on pc The module prj21 update to firmware V3, but I have only in step 7 the product versions 1 and 2.
I made a diagnostic to de cp and appear this error: Follow us on Twitter Youtube. The GSD file you will find here: If this is already done, it would be good to see how they have been configured. I uploaded the file already. In the front of the module apeare that is the version 2.
But it’s possible that the problem is the hardware config. I can now use diagnostic option and I can see states of plc and module.
CX-Configurator CJ1W-PRM21 connection problems.
What I can do. What about those errors? Sign in Already have an account?
Am I missing CX-Server? When i try to use scan option i get another error:.
Share this post Link to post Share on other sites. I’m almost sure that this bosch unit provides profibus connection. When i try to use scan option i get another error: Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community. Hello Daniel, Thanks for your answer.
Try to run the AutoUpdate so you’ll get a newer version if you have a registered copy. When I use “Test” option or just go online I get errors: Site Explorer Site Explorer.
This contribution was helpful to 1 thankful Users dchartier. The master tell me that the slave have a invalid response. I have no idea. Edited 21 March by malyalewariat. It is profibus slave. All about Decentral Peripherie.
Sign In Sign Up. The number of bytes its going to recive and send. I also programed the functions send and recv acording with the master configuration. It supposed to be toolbus usb in configuration tab, and now i can use test, and go online options without any errors. I was sure that I’ve tried all but I didn’t. Started by malyalewariat18 March. Product Support Services Forum mySupport. pm21
Have a look at the following FAQ and attached links: Hope this helps, Daniel Chartier. I configured in S7 project the slave parameters. Sign up for a new account in our community.
Register a new xj1w. You need to be a member in order to leave a comment. So many communication protocols to choose.